New Lennox SLP98v unit is flashing the code A375. Any idea what that means?Post created: 2014-06-01 Type of Equipment: Furnace Views: 312
This question was created on the page: https://www.furnacecompare.com/furnaces/lennox/slp98v.html.
Owned less than 1 month. Problem appeared today, to me. I have tried nothing to fix.
On 2014-06-02 Danielle wrote:
According to the Installation Manual for the Lennox SLP98v the diagnostic code of "A" is displaying the Cubic feet per minute (cfm) setting for indoor blower (1 second ON, 0.5 second OFF) / cfm setting for current mode displayed.