What does four flashing red lights indicate on a York Affinity 8.S furnace?Post created: 2016-01-15 Type of Equipment: Furnace Views: 190
This question was created on the page: https://www.furnacecompare.com/furnaces/york/affinity-8.s.html.
On heating cycle the furnace stops short of set temprature. Usually happens around 61 to 62 F. The set temprature is 68 or 70. When the furnace stops i see four flashing red lights on the control board.
On 2016-01-15 Gary wrote:
Four red flashes indicates that a high-limit switch is open. This can be caused by something restricting airflow, such as a dirty air filter or a problem with the ductwork, as well as a problem with the control board or the blower motor.
If this problem is something you'd like to have a contractor take a look at, we can help you find one, here.