I have a Trane XV80 furnace. Is there a filter in the furnace? I have two filters in the house but I thought there was one in the furnace compartment.Post created: 2014-12-16 Type of Equipment: Furnace Views: 399
This question was created on the page: https://www.furnacecompare.com/faq/which_filter.html.
On 2014-12-17 Danielle wrote:
Typically when furnace filters are found in the furnace cabinet the air flow configuration of that unit is upflow. Most downflow units have their filters in the ductwork.
See the chart below for matching filter for the Trane XV80. The correct filter matches to the air flow configuration and cabinet width.
Furnace Filters for the Trane XV80
|Air Flow Configuration||Cabinet Width||Filters|
|Upflow||17-1/2"||1 17x25x1 filter|
|Downflow / Horizontal||17-1/2"||2 14x20x1 filters|
|All||19-1/2"||1 17x25x1 filter|
|Upflow||21"||1 17x25x1 filter 1 20x25x1 filter|
|Downflow / Horizontal||21"||2 16x20x1 filters|
|All||23"||1 20x25x1 filter|
|Upflow||24-1/2"||1 17x25x1 filter 1 24x25x1 filter|
|Downflow / Horizontal||24-1/2"||2 16x20x1 filters|
|All||26-1/2"||1 24x25x1 filter|
|Upflow / Horizontal||All||2 16x20x1 filters|