I got a Dunkirk #95M-200 when I turn off for summer and when turn it back for winter on the panel it got E-04 and will not run what is the cause?Post created: 2014-11-03 Type of Equipment: Boiler Views: 197
This question was created on the page: https://www.furnacecompare.com/boilers/index.html.
4yrs year after Igot it the contr. come reset it
On 2014-11-04 Danielle wrote:
According to the manual for the Dunkirk 95M-200 a diagnostic code of E-04 means "Voltage lost after lockout occurred". The solution is "Control module will only restart with manual reset, even after power loss (but the error code information is lost)."
Below is a copy of the manual.