Air filter replacement for the Trane XE90.Post created: 2014-08-31 Type of Equipment: Furnace Views: 291
This question was created on the page: https://www.furnacecompare.com/furnaces/trane/xe90.html.
On 2014-09-02 Danielle wrote:
The filter you need depends on both the configuration of the furnace (see this page: http://www.furnacecompare.com/faq/definitions/air_flow_configuration.html) and the width of your furnace's cabinet. See the chart below.
Please let us know how you make out!
Furnace Filters for the Trane XE90
|Air Flow Configuration||Cabinet Width||Filters|
|Downflow / Horizontal||17-1/2"||1 14x20x1 filter|
|Downflow / Horizontal||21"||1 16x20x1 filter|
|Downflow / Horizontal||24-1/2"||1 16x20x1 filter|
|Upflow / Horizontal||All||1 16x20x1 filter|