We have a Carrier Performance 80 58CTA110-1012 furnace with air conditioner. How do we control the fan speed?Post created: 2014-07-16 Type of Equipment: Furnace Views: 446
This question was created on the page: https://www.furnacecompare.com/furnaces/carrier/performance-80.html.
On 2014-07-17 Danielle wrote:
To control the fan speed in your Carrier Performance 80 the following instuctions were found within the manual (http://dms.hvacpartners.com/docs/1009/Public/01/OM58-131.pdf):
Comfort Fant --On all but the 58STA or 58STX, the continuous fan blower speed can be increased or decreased if desired due to change of seasons, large gatherings in your home, etc. Simply change your FAN switch from on to off (or auto depending on your thermostat), and then return to on, within 1 to 3 seconds. The blower will switch to the next highest speed. There are at least 3 speeds to choose from. If the blower is running on its highest speed, a request to change will direct the blower to return to its lowest speed.