Does our Trane XV80 require a filter into the furnace itself? Our installer said no, only one in the house. This doesn't seem right.Post created: 2014-06-20 Type of Equipment: Furnace Views: 187
This question was created on the page: https://www.furnacecompare.com/furnaces/trane/xv80.html.
Need to know if our TRANE XV80 requires a filter going into the furnace itself. Our installer said we only need a filter for the inside of the house. If it does require such a filter into the furnace itself, what are the order numbers and the cost?
On 2014-06-24 Danielle wrote:
According to the installation instructions on pages 8 - 13 it does require bottom and side filters. For the manual see the link below. For filters see the chart below.
Let us know how you make out!
Furnace Filters for the Trane XV80
|Air Flow Configuration||Cabinet Width||Filters|
|Upflow||17-1/2"||1 17x25x1 filter|
|Downflow / Horizontal||17-1/2"||2 14x20x1 filters|
|All||19-1/2"||1 17x25x1 filter|
|Upflow||21"||1 17x25x1 filter 1 20x25x1 filter|
|Downflow / Horizontal||21"||2 16x20x1 filters|
|All||23"||1 20x25x1 filter|
|Upflow||24-1/2"||1 17x25x1 filter 1 24x25x1 filter|
|Downflow / Horizontal||24-1/2"||2 16x20x1 filters|
|All||26-1/2"||1 24x25x1 filter|
|Upflow / Horizontal||All||2 16x20x1 filters|