Troubleshooting and Repairing your Boiler
Published Sep 19, 2016
By Gary Sprague
If your boiler stops running, here are five troubleshooting steps you should take before doing anything else:
- Check that the emergency shut off switch hasn’t been turned off by mistake. The switch looks like a regular light switch but with a red cover plate. You should have two switches – one mounted on the side of your boiler, and one near the top of your basement stairs or near the door of your boiler room.
- Check for a bad fuse or tripped breaker in your main electrical panel.
- Check to be sure that you haven’t run out of propane or oil.
- Make sure the thermostat is on and set to “Heat”. Check that the temperature setting is not too high or low. Also check the thermostat batteries and change them if needed.
- Press the red reset button, usually located on the burner at the front of the boiler. If your boiler shuts down for some reason, a simple reset may be all it needs to get running again.
These are simple steps, but they can save you an embarrassing and potentially expensive service call. Here are a few other common boiler problems:
No Heat from Radiators
A bad circulator pump or zone valve can cause this problem. Air in the pipes is another common reason for cold radiators. If there are bleeder plugs on your radiation you can loosen them to let the air out. If not, the entire zone where you have no heat will need to have the air bled out. This can sometimes be done by the homeowner, but flushing air from heat pipes can be tricky and will often require a call to your heating contractor.
Pilot Light Won’t Stay On
This is usually caused by a damaged thermocouple that will need to be replaced. It can also be caused by a draft blowing the pilot out, or a dirty flame sensor. A flame sensor is fragile but can be easily cleaned using steel wool or fine sandpaper to clean the rod.
A Noisy Boiler
Noises such as banging, knocking or gurgling can be a sign of air in your heat pipes. Air is a common cause of boiler problems. The sounds can also be caused by "kettling", which is a buildup of mineral deposits in the heat exchanger. Bleeding your pipes will usually help with the noises. If not, your heating contractor can use a chemical additive to get rid of the deposits.
A boiler leak can come from the pipes leading to and from the boiler, from one of the fittings threaded into the boiler, or from a crack in the boiler. Most boiler leaks require shutting down and often draining the system and will need to be repaired by a heating professional.
Having your boiler serviced annually can help prevent many problems. Soot can build up and components can wear over time, but an annual cleaning and adjustment can keep your unit functioning properly for many years. Always keep the manufacturer's manual handy and if you don't have one, request one from the manufacturer.