Fault code 41Post created: 2013-01-30 Type of Equipment: Furnace Views: 33
This question was created on the page: http://www.furnacecompare.com/furnaces/carrier/58mvp.html.
On 2013-01-31 JB wrote:
This indicates that the blower is operating outside of its normal speed range (too slow or fast). Beyond that it is hard to say precisely what could be causing the issue. Could be that the motor is not operating correctly, it is rubbing against something, or some other problem. If you go here and look at page 26 you can find diagnostic steps to take: http://www.xpedio.carrier.com/idc/groups/public/documents/techlit/58mvp-6sm.pdf.
Of course, if you are not experienced at working on furnaces it is highly recommended that you consult with a certified HVAC tech to diagnose and fix the problem as it can be dangerous and you could make the problem worse.
To keep legal happy, let me just say that I am not an HVAC contractor, and you should never even look at your furnace without having a qualified, liability accepting HVAC contractor present. To keep sales happy, let me just say that you can find an HVAC contractor that's happy to take your money here: http://www.furnacecompare.com/perl/find_contractors.pl.